Purchasing Guide for Sepehr Electric Tuck Water Cooler
- Using water coolers in the zones with warm and dry climate in the summer is suitable, but they are not suitable for the zones with warm and wet climate (sultry).
- Water coolers furnished with top intake aeration known as balcony coolers are mainly designed and produced to be installed in apartments balconies regarding air duct outlet canal location (from top).
- For approximate calculation of required water coolers capacity under climatic conditions such as Tehran, use Water Cooler Model SE 400, Sepehr Electric for apartments with an area of 85 Sqm. which are constructed in the middle of building and are not exposed to sunlight and their cooler duct work was on correct method, and use Water Cooler Model SE 600, Sepehr Electric for apartments with an area of 150 Sqm.
- In case apartment demanded by you is located on the top floor whose ceiling is directly exposed to the sunlight in the summer, by observing other above conditions, use Water Cooler Model SE 400, Sepehr Electric for apartment with an area of 75 Sqm. and use Water Cooler Model SE 600, Sepehr Electric for apartments with an area of 140 Sqm.
- The dimensions of water cooler should be calculated more wide open than air outlet, otherwise air exposed to condensation resulted in flow backward it manes the larger size, the less static pressure thereby more airflow and cold generated by the water cooler.
- The rate of airflow and cold air generated by water cooler fully depends on observance of duct work course engineering services principles and generally Installation Engineers should perform calculations of cooler duct work by using ductulator and considering route angle changing ( Intrados radius) and change of canals dimensions (maximum with angle 15º), otherwise, you should not expect cold air. As it was observed, at present, the customers resort to other cooling and high consumption systems such as splits due to the same defect.
- Sepehr Electric Tuck Water Coolers are provided with a 1-year warranty.
The points should be taken into consideration after purchasing Sepehr Electric Tuck Water Cooler
- Regarding air pollution and water salts which cause sedimentation shell and packing of air-conditioner , the packing should be exchanged after 1500 hrs. performance and or at least annually at the beginning of start-up season.
- Prevent from direct sunlight on air-conditioner by installing a sunshade on which and it is necessary to insulate air-conditioner duct in case more than 2 m. of length of which is exposed to sunlight.